Area Of Applications
UV System Selection
Sizing of correct UV unit depends on factors including
- Desired UV Dose
- Peak flow rate
- %UVT10 of water
Advance ADV-FM™ Series for water with 80-98%UVT
The table below shows Advance ADV-FM Series UV units for EOL (end of lamp life) UV Dose of 60mJ/cm2 (600J/m2) @90%UVT10 for chloramines reduction in swimming pools.
Contact us for UV system sizing based on other combinations of Peak Flow Rate, %UVT & UV Dose Requirement.
|ADVANCE ADV-FM™ SERIES UV SYSTEM||PEAK FLOW @600 J/M2 [Ltr/Min]||PEAK FLOW @600 J/M2 [M3/HR]||ELECT. POWER [KW]|
|ADV-FM 25|| 333.33||20||1 KW|
|ADV-FM 550|| 7,000.00||420||12KW|
Advance ADV-FM™ and ADV-FM™ LT™ Series Spare Parts
Contact us for Advance UV lamps, Advance UV quartz sleeves, Advance UV ballasts, Advance UV O rings, Advance UV sensors and Advance UV spare parts. We would be delighted to put you in contact with Advance UV resellers for Advance ADV-FM™ spares & service.
Advance ADV-FM™ Series: Technical Summary
|OPERATING PARAMETER||GENERALLY RECOMMENDED RANGE|
|Peak Flow Rate (m3/hr) [Note1]||30m3/hr to 420m3/hr|
|Peak Flow Rate (lpm) [Note1]||500lpm to 7,000lpm|
|%UVT10||80% to 98%+|
|Operating Water Pressure (kg/cm2)||1kg/cm2 to 6kg/cm2|
|Operating Water Temperature||4dec C to 45 deg C|
|Input Power Required||415V AC, 3 phase|
* Contact us for model selection to suit your application
Note1: Recommended peak flow rate depends on factors like desired EOL UV Dose, %UVT of water, etc.
UV-Guard, Wedeco, Wedeco AVP, Australian Ultra-violet Products (Mfg) Co., Sterilight, R-Can, Trojan, Aquafides, etc. ultraviolet lamp & ultraviolet system manufacturers` brand names, trademarks and logos belong to their respective owners and while we make reference to the ultraviolet lamp & ultraviolet system brand names, we are in no way endorsed by or associated with these companies who sell ultraviolet disinfection systems, ultraviolet lamps, Quartz Sleeves, UV lights, germicidal lamps, UV bulbs, Quartz Sleeves, Quartz Tubes, Quartz Thimbles, etc.
UVT of water, etc.
Spares & Service
Advance UV Systems Pty. Ltd.
Unit 22, 17A, Amax Ave
Girraween NSW 2145
- Phone No: +61 (0) 2 9896 1165
- Fax: +61 (0) 2 9896 4465
- Email: email@example.com